The servers in the TSRB MDF are unavailable.
WHEN DID IT HAPPEN?
At approximately 8:45 AM Tuesday, June 12, 2011.
WHY DID IT HAPPEN?
The cause is currently unknown.
WHO WAS AFFECTED?
CoC faculty, staff, and students attempting to use the affected servers. Users of svn.cc.gatech.edu.
WHAT DO YOU NEED TO DO?
No user action is required.
HAS THE PROBLEM BEEN RESOLVED?
No. TSO is investigating and will restore services as soon as possible.
WHO SHOULD YOU CONTACT FOR QUESTIONS?
TSO Help Desk (CCB 148, 404.894.7065, firstname.lastname@example.org)
UPDATE: The power distribution unit (PDU) received a power overload at 8:30 AM 7/12/11. It tried to bypass to battery backup, but the bypass module failed and the PDU shut down. The PDU has been restarted and services have been restored as of approximately 11:20 AM 7/12/11.